SGH visited the site to observe the flooring condition. We measured the relative humidity, vapor emission rate, and pH of the concrete slab. SGH collected cores and samples of the crushed stone layer below the slab. We performed the following testing in our laboratory:
Determined the moisture content of the crushed stone
Conducted Fourier transform infrared spectroscopy to identify the constituents of the adhesives
Performed petrographic analysis to examine the characteristics of the concrete slab and the cementitious underlayment applied to the slab surface
SGH observed adhesive from a previous carpet installation remaining between the new underlayment and the concrete slab. The underlayment did not bond to this adhesive, leading to bubbles and wrinkles in the flooring. We also concluded the floor tiles lack a continuous application of adhesive and are poorly bonded.
We recommended removing the flooring assembly down to the concrete slab, preparing the concrete substrate, applying a new cementitious underlayment, and installing new adhered floor tile.