SGH determined that water infiltration through the open head joints in the gable coping stones caused heavy mortar deterioration in the gable walls. The brick gables were rebuilt with a reinforced masonry backup. We also observed that the clock tower roof had missing and loose slate and the copper cap was worn thin and missing copper leaves at its base. We determined that connector roof on the addition had failed.
We developed a prioritized repair scope, produced construction documents for the flat roof replacement and for repairs to the original building masonry gables and slate roofs, and monitored construction. Repairs included the following:
- Replicating brick veneer, including the basket weave and articulated brickwork patterns
- Repairing and reinstalling original brownstone, stone, and terra-cotta features
- Removing the existing slate and copper roofs, reinstalling existing slate with some matching replacement slate, and replicating the copper cap in-kind
- Repairing the wood roof deck and the structure supporting the weathervane during the roof replacement work
- Replacing low-slope membrane roofs and perimeter flashing